- Exdirt V is the ideal solution for using the classic reflex dirt and sludge separator Exdirt in vertical lines, too.
- Standard mounting sizes according to series F1 and F2 (DIN 3202-1) according to DIN EN 558: 2012-03 allow for easy installation in existing facilities.
- In order to protect the facility, an Exdirt should be installed in un-renovated sections of an existing heating system in order to minimize the dirt load for the system.
Installation of the generator circuit pump
- The generator circuit pump should not be installed directly on the manifold in order to avoid faulty currents and exerting pressure on the manifold.
Reflexomat double compressor system
- The double compressor and also a pump for redundancy or to increase the performance of the pressure raising system.
Quality of pressure maintenance
- Reflexomat and Reflex Servitec—the ideal connection! Combine the Reflexomat with the Servitec spray tube degassing system. It not only does the make-up and frees the make-up water from dissolved gas, but also ensures almost gas-free system and make-up water. Air problems from free gas bubbles at system hot spots, circulating pumps or control valves are thus reliably avoided, and corrosion problems effectively prevented.